Tags: HOT START UP AFBC BOILER, light up of afbc boiler, WARM In this article we discussed about the AFBC boiler hot startup and cold. The start up of fluidised bed combustion boilers has always been a subject of the most surface, it is advised not to proceed with the light up. Unless the top. Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO
|Published (Last):||27 June 2007|
|PDF File Size:||2.70 Mb|
|ePub File Size:||15.12 Mb|
|Price:||Free* [*Free Regsitration Required]|
Feed pump and drives. Cfbc Boiler s,ebooks and documents of cfbc boiler operation manual thermax – afbc boilers, Ensure all personel were cleared. Cfbc bolier operation procedure? Fuel feeders and controllers.
Add gas plenum pressure P2 Furnace draught to P1. Boiler light up procedure A fixed quantity of dry charcoal Kgs i. Light up all the four burners. Bed material Maximum Particle size Bulk density Chemical composition: Keep the PA lines clear and take trial run of feeder of first compartment. Afbc Boiler Operation Manual – ante-annum. Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet.
Start the FD fan and maintain bed pressure mmwc. Boiler Manual For Cfbc – boiler operation procedure? After stabilisation of bed temperatures stop the burners and LDO pumps.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Boiler Installation – Afbc Documents. Afbc Boiler Operation Manual – boiler operation procedure 1 seminar lighr boiler operation procedure,Ask Latest information,Abstract,Report,Presentation free download cfbc Documents.
Feed control valve and its bypass valve. CFBC boiler operation procedure? Inspect the boiler before start and check Manual on Boiler Tube Bhel steam generators products afbc boilers Tags: Inspect the boiler before start and check the following 1.
Check the bed material and fludisation study is being done. Close the bed superheater drains. Bed material to be filled and level of defluidised bed should be MM of WC.
Afbc Boiler Light Up Procedure
Cethar Afbc Boiler Manual – dire searching for a afbx Cethar afbc boiler manual in Start the LD oil pump and maintain the oil pressure between 6. All interlocks to be cross checked. Ensure all access doors are closed. Afbc Boiler Operation Manual – boiler operation manual at The air flow at which fludisation starts is noted and will be maintained at the time of mixing.
Check the following equipments for adequate lubrication. Ensure the deaerator water level as normal. Valves before and after feed control valve in feed line. Drum and main line vent. Set the air flow to MM of wc P.
C and start the ash handling system. Drain valves of water level gauge. When the bed temperatures reaches Deg C start the drag chain coal feeder. Once fludisation study is completed boiler is ready for light up. Valves on feed line connecting to feed pumps operation.
Check the following valves are kept in open condition.
Check the following valves in boiler are in closed condition. Main steam stop and pilot valve. Afbc Boiler Operation Manual – snowman-ro.
Published on Oct View 3. Maintain drum level at normal recommended level. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing. Measure air box pressure P1 MM of wc 3. Ensure all foreign materials are removed from furnance and pressure parts. Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser.
The pressure drop across bed is obtained for various air flow. Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
C and stable the boiler. Turn off the oil burners and remove from furnace.